€37.43 net €31.45
€53.75 net €45.17
€128.56 net €108.03
Shipping in 21 day(s)
€97.62 net €82.03
€39.28 net €33.01
€131.59 net €110.58
€114.81 net €96.48
Shipping in 3 day(s)
€142.56 net €119.80
Shipping in 3 day(s)
- Comprehensive advice & support
- Free shipping from 50 € order value
- Shipping in 24 hours
- thousands of satisfied customers
KATHRIN BRANDTEmployee Purchasing from Troisdorf
Great advice and friendly service. I was helped immediately and competently with any questions. Gladly again.
OMAR NASEROffice Manager from Frankfurt a.M.
Goods are well packaged and arrive safely, which is important to me. My mail was answered immediately.
RAINER SEIDELMaster carpenter from Wiesbaden
Had to replace a lamp, but the same was no longer available. Great advice, found a suitable replacement and delivered it quickly.
Emergency lighting is lighting that takes effect in time when the general power supply of artificial lighting is disrupted. It is the generic term of backup lighting and safety lighting.
The purpose of the replacement lighting is to continue the current activity which cannot be interrupted for certain reasons (e.g. during operations in hospital).
Safety lighting is divided into
- emergency lighting of escape routes (for safe recognition of escape routes and safe exit from rooms)
- anti-panic lighting (to reduce the risk of panic in large gatherings of people, such as open-air concerts, major night-time events, in spectator areas at indoor sports events, etc., as well as in department stores, for example, and to provide adequate visual conditions for orientation and safe walking to escape routes)
- safety lighting for workplaces with special hazards (for safely ending activities and leaving the room).
Replacement lighting should allow work to continue undisturbed - if necessary, even for a limited period of time.
If the activity is to be carried out even after the general power supply has failed, the photometric requirements for the back-up lighting result from the nature of the activity and the visual performance derived from it during the period of normal power supply.
However, if the activity is to be shut down (terminated) within a reasonable time, lower lighting requirements may be accepted. Although EN 1838 does not specify this in detail, at least 1⁄10 of the illuminance maintenance value prescribed for normal conditions is required. Switchover usually takes place without interruption within 0.5 seconds.